You can still browse the site but some services may not work properly. This site requires Google Chrome, Firefox, Safari or Internet Explorer 10 and above. For mobile devices use an HTML5 capable browser.Download Chrome
In Part 4, we looked at two of the four methods for determining the correct rating for a motor controller.
The third method is one you can use for stationary motors of 2HP or less and 300V or less [430.83(C)]. You can use a general use switch or a general use snap switch to control the motor:
The fourth method applies to torque motors. In these applications, the controller must have a continuous-duty, FLC rating at least that of the motor nameplate rating [430.83(D)].
Section 430.83 ends with one last requirement, but it’s not a method. It applies to whatever method you’re using. Basically, it says the voltage rating of the circuit can’t exceed the voltage rating of the controller [430.83(E)].
Now, here’s another fact about controllers. An overcurrent protection device (OCPD), such as a circuit breaker, must open all conductors of the circuit. But that’s not a requirement for a motor controller [430.84]. Why the difference? The controller need only stop the motor, while the OCPD must de-energize the circuit.