You can still browse the site but some services may not work properly. This site requires Google Chrome, Firefox, Safari or Internet Explorer 10 and above. For mobile devices use an HTML5 capable browser.Download Chrome
Part IV of Article 440 provides the requirements for branch-circuit conductors used with hermetic motors.
These requirements are intended to be used as a companion to the requirements in Article 310. That means your design basis is Article 310, but you will refer to Article 440 for amendments and additions to the Article 310 requirements.
As with other motor circuits (covered in Article 430), the load calculation depends upon whether the branch-circuit supplies:
And there’s this provision that applies to the last two above [440.33]. For all the motors, add up the motor-compressor rated-load currents, then the branch-circuit selection currents. Add whichever is greater to the sum of the full load currents of the motors, plus 25% of the highest motor or motor-compressor rating in the group. Two Exceptions apply [440.33].
Source: Mark Lamendola | Mindconnection