You can still browse the site but some services may not work properly. This site requires Google Chrome, Firefox, Safari or Internet Explorer 10 and above. For mobile devices use an HTML5 capable browser.Download Chrome
In our previous issue, we said that LV systems must be listed as complete systems. Any listing requirement depends upon the conditions of use. The NEC poses limitations on these systems in certain locations [411.5].
If you install an LV system in:
Article 411 also puts limitations on secondary circuits [411.6]. But it does not define what these are, nor is there a definition in Article 100. So what are they? Remember, LV systems require a low voltage power supply. The circuits coming off the secondary side of this transformer are secondary circuits. The circuit that feeds the primary side is a branch circuit (max 20A).
The transformer itself must be an isolating transformer that separates the branch circuit from the secondary circuit [411.6(B)]. Now, one thing you don’t want to do is couple the two sides by bonding one of the secondary conductors to ground. So the NEC explicitly prohibits doing that [411.6(A)].
If the installation is indoors, you can have bare conductors [411.6(C)]. But they must be at least 7 feet above the finished floor unless specifically listed for a lower installation height.